If you want to integrate an HVAC system with a limited number of split units with the TELETASK home automation system at an economic price, the HVAC PLUG interface and HVAC HUB may be the best choice. Thanks to this wired integration directly from the PLUG interface to the indoor unit, the end-user can manage his HVAC indoor units from the TELETASK touch screens and mobile devices.
See also this guide for more information.
3. Connect the HUB with the LAN (same as TDS central unit)
4. Set a fixed IP address in the HUB
- Download, run and install the QuickInstall Setup
- Now select the 'SetupUtility' (2.2.4 or higher)
- In the menu 'connection > network > discover devices' - connect - set IP to static - enter IP address (...) + 'Apply'
5. Search the PLUG addresses to use in PROSOFT
- See LCD display on the HUB unit OR use the SetupUtility (Terminal > ls)
- Example address: L2.198
6. Add the TDS15200 in PROSOFT (supplied with the HUB interface)
- Select the interface TDS20068
- Add the sensor zones with their proper address (see above) ex: L2.198
- In the rooms list (PROSOFT) add the concerned sensors to the rooms
7. Transmit your .nbt file to the central unit
Table of contents: